The spectrograms of the microphone (ENV_EDB_MIC) and accelerometer (ENV_EDB_ACC) make in evidence the acoustic and seismic noise variations in DET-Lab after the last actions to set-up the supply inverter frequency of that air handling unit (AHU), Figure 1 and Figure 2. In both spectrograms, a significant noise reduction is visible after each inverter frequency reduction action. The rms signal of the microphone shows a noise reduction of about 40% in the band (1-16)Hz and of about 70% in the band (16-512)Hz having set up (step by step) the supply inverter frequency from 45 Hz to 35 Hz, Figure 3.
Moreover, the evidence of noise reduction is visible also in the other attached Figures concerning the acoustic and vibration sensors, also in the squeezing area (ENV_EQB1*). General important noise mitigation was achieved in the bandwidth ~(10-100) Hz, Figure 4, 5, 6,7, 8.
More analysis will follow.