soldani - 18:04 Tuesday 24 March 2020 (48797)
Print this report
The low level of humidity in DET Lab today was due to the clogging of the steam-pipe inside the air handling unit. Proof of this was the production of 100% effective steam but the relative humidity in the air tube does not increase beyond 60%.
The external maintenance firm tried to clear of limestone inserting a special probe from the outside. A special inspection is needed inside the air handling unit.(to be scheduled).